NEW! COVID-19 Products
Below are the available bulk discount rates for each individual item when you purchase a certain amount
- Buy 12 - 23 and get 4% off
- Buy 24 or above and get 7% off
Ansul Met-L-Kyl Class D fire extinguishing agent is a sodium bicarbonate-based dry chemical specially designed for suppressing fires involving most metal alkyls (pyrophoric liquids which ignite on contact with air) such as triethylaluminum. For small quantities, many people apply this agent with a scoop or shovel, but for larger quantities we suggest an actual extinguisher to give you stand-off fire fighting ability; see below for details. The 50 lb pail is Ansul part # 9329.
Caution: MET-L-KYL DRY CHEMICAL SHOULD NOT BE USED ON FIRES INVOLVING COMBUSTIBLE METALS such as magnesium, sodium, potassium and sodium-potassium alloy (Nak). Its use would cause an already intense combustible metal fire to burn even more violently.
The shipping weight of this item is 54 pounds (24.5 kg) and there are 36 containers per pallet. Given the heavy weight, a fixed shipping charge of $20 per container will be applied to your order at checkout which is valid only for ground shipment within the lower 48 US states. If you need rush delivery or delivery outside this area, you can contact us before ordering, otherwise, we will contact you with the actual freight costs before processing your order.
Downloads available: Safety Data Sheet (SDS) for Met-L-Kyl.
Application Note: Initial application of MET-L-KYL dry chemical extinguishes the flame and continued application adsorbs the remaining fuel and prevents reignition. With this method, 10 pounds of triisobutylaluminum and 10 pounds of tri-n-propylaluminum, both in depth, were extinguished using 80 pounds of MET-L-KYL dry chemical applied from 350 pound capacity wheeled extinguishers. Ten pounds of triethylaluminum in a spill and in depth were extinguished using 100 pounds and 80 pounds of MET-L-KYL dry chemical applied from 30 pound capacity extinguishers. MET-L-KYL dry chemical caused a slight decomposition of the triethylaluminum during application, but this did not hinder extinguishment.
The ratio of pounds of MET-L-KYL dry chemical to pounds of any one of the three trialkylaluminums used ranged from 8:1 on fires in depth to 10:1 on spill fires. Quite a bit of the dry chemical was carried away by the fire’s updraft during the initial flame extinguishing phase. This accounts for the large amount needed for complete extinguishment.